Momentary contact wall switches
Search by 5-digit Product Code
MINI Ceiling-mount detectors
MINI Ceiling-mount detectors >>
MINI secondary sensor for use with any PP power packs (requires primary sensor on same power pack)
One MINI primary sensor is required on the same power pack for the MINI-S-PP-W-FC to function. Refer to tech sheets for part number 97190, 97191 and the appropriate power pack.
Designed for wet and high-humidity locations
Works with the B.E.G. PP series power packs or proprietary low voltage system
Up to 4 Secondary sensors may be connected with a primary sensor to increase motion detection coverage. 2-way male to female RJ-12 splitter included.
Spring clips for quick and easy installation in suspended ceilings and light fixtures
5 years limited warranty
Masking blinds included
Programmable features cannot be adjusted via the secondary sensors, only the primary sensor.
ROHS and REACH compliant
To maintain the wet location rating the back of the sensor must not be exposed to wet locations (must be installed in a covered ceiling, a fixture with a wet location rating, or in an IP65 or NEMA 4 enclosure).
Private and Open Offices Conference Rooms School/University Classrooms Corridors Healthcare and Laboratory Spaces
Open air parking garages Under outdoor canopies Sally ports Loading docks Vacancy (Manual) operation is achieved by combining the MINI primary sensor, MINI-S-PP-W-FC, and PP power pack with a low voltage momentary contact switch. For high mounting applications please refer to MINI-S-PP-GH-W-FC, part number 97197.
Operating voltage: 24 V DC from B.E.G. Controls Power Pack PP-1-J or PP-A-J, or compatible power supply by others. Please contact B.E.G. Controls to confirm compatibility with power supplies by others.
Power consumption: 1 W
-13 °F to 122 °F / -25 °C to +50 °C
UV- and shock resistant 5VA material
Cable length: 9.8 ft / 300 cm
Compliances: ETL listed for the U.S. and Canada (UL STD 60730-1 and CSA STD E60730-1). UL 2043 plenum rated.
Specification Details [...]
Copyright: ® 2018-05-27 - B.E.G. Controls